As we continue our recovery and cleanup efforts, please visit the Emergency website for the latest information on openings and closings in Miami-Dade County.
Meeting the new requirements of PA201, PA202, and PA203
The following depicts how that may be accomplished.
First, the importance factor to be used when designing to ASCE 7-88 is 1.05. The walk-in coolers need to be tested for impact and cyclic loading, where the cyclic loading has corresponding structural design load multiples. If your design incorporates a roof design or material type that is covered in the Miami-Dade County Roofing protocols, it would have to be tested under that protocol. Also, a live load test may also be required per section 2314.2 of the South Florida Building Code.
Second, the following depicts some of the configurations that would be required in order to comply with the established requirements.
The depicted X1, X2, and X3 correspond to the two impact locations of each of the three wall specimens required.
The X depicts the location of the two required impact locations on each of the three roof specimens required.Back to Top Page Last Edited: Wed Jul 10, 2013 1:45:57 PM
You are now leaving the official website of Miami-Dade County government. Please be aware that when you exit this site, you are no longer protected by our privacy or security policies. Miami-Dade County is not responsible for the content provided on linked sites. The provision of links to these external sites does not constitute an endorsement.
Please click 'OK' to be sent to the new site, or Click 'Cancel' to go back.